Fire Protection Supplement
Fire Protection System Inspection, Testing,
and Maintenance Procedure
Jefferson Lab conducts regular inspections, periodic testing, and preventive maintenance of its fire protection systems to ensure their continuous, proper operation.
Inspection, testing, and maintenance (IT&M) are conducted in accordance with the National Fire Protection Association (NFPA) requirements supplemented by equipment manufacturers' recommendations. Fire protection IT&M requirements shown in this supplement are derived from the reference documents listed below.
This document describes the use of subcontracted service work, quality assurance, and corrective actions employed to inspect, test, and maintain installed fire protection equipment. Timing of these activities is influenced by accelerator operations and available access times.
Fire protection system maintenance is an element of the Facilities Management and Logistics Department (FM&L).
3.1 Fire Protection Engineer (FPE)
· Functions as the Subcontracting Officers Technical Representative (SOTR) for fire protection contracts.
· Maintains the IT&M documents to industry standards.
· Ensures quality assurance activities are accomplished.
· Analyzes reported deficiencies in fire protection systems to prioritize corrective actions or major maintenance.
· Investigates malfunctioning fire protection equipment to determine corrective action needed.
· Oversees the daily activities of subcontractors’ staff for inspections and tests in accordance with the procedures contained in this document.
· Coordinates the required IT&M activities with area work coordinators using the regional electronic work control system for each area.
3.2 Fire and Security Technician
· Investigates malfunctions in the NCC alarm monitoring network and coordinates corrective action.
· Investigates malfunctions in the VESDA network and coordinates corrective action.
· Assists the FPE with fire protection system modifications and additions as requested.
4.1 General Fire Protection Information
Several documents are required to accomplish all aspects of inspection and testing. The following documents contain tables and lists of detection and suppression devices located throughout the Jefferson Lab Facilities.
o A comprehensive list of building and pertinent fire protection features. This document contains the following information for each Jefferson Lab building:
§ Building name and number;
§ Building use, floor area, number of stories and construction type;
§ Fire suppression systems general description;
§ Fire detection and alarm systems general description; and
§ Estimated values of buildings and administrative contents.
o Multiple comprehensive spreadsheets listing fire detection and fire suppression devices contained in each building.
o A list of portable fire extinguishers located throughout the site.
o A site plan showing 32 fire hydrants located on the private service fire mains within Jefferson Lab.
o A list of early warning smoke detection devices.
4.2 Inspection Requirements
Several documents convey the required inspections to be performed on each fire protection device.
o The naming convention for fire protection identifiers used in a computerized maintenance management system.
o A detailed list of periodic inspections and tests that apply to detection and suppression system devices.
· Maintenance Reports
o A tabulated list of specific fire protection devices using designator codes and PM inspection codes generated by the computerized maintenance management system.
4.3 Test Requirements
Several fire protection devices require periodic testing to demonstrate continued satisfactory performance. Each test requires data to be recorded. Testing procedures are written for.
4.4 Subcontracted Service Work
IT&M of fire protection systems are performed by both Jefferson Lab staff and subcontracted fire protection services. Service work on sprinkler systems, alarm systems, hand-held fire extinguishers, and hydrant/water supply systems is performed by subcontractors. Services normally include performance of maintenance inspections or tests, submittal of records, inspection forms or deficiency reports. The FPE, under the direction of the Facilities Management Director, specifies and approves vendor and staff qualifications before work begins.
The current IT&M subcontract is:
· P. O. #JSA-13-C0801 for The CFP Group.
See the Performance Work Statement for additional information regarding subcontracted services.
4.5 Quality Assurance
Quality assurance for subcontracted fire-protection services is accomplished through the Quality Assurance Plan contained in the subcontract document.
For quality assurance forms see either Inspection of Services (Contractor Performance Evaluation) or Quality Assurance Report and Quality Check List.
4.6 Deficiencies and Corrective Actions
Equipment found to be malfunctioning with respect to intended design, condition, and function in fire protection systems are considered a deficiency. The FPE promptly analyzes reported deficiencies and assigns an appropriate risk code, which governs the prioritization of corrective actions.
Deficiencies reported through inspection and testing activities are entered into the FM&L Work Order System for tracking through completion. An impairment action is implemented based on hazard analysis.
5.0 Inspection, Testing, and Maintenance
Fire protection maintenance activities are conducted in accordance with the FM&L subcontract for the identified IT&M work. Complete records of all testing, inspection, and maintenance activities are maintained by the FPE. The frequency of IT&M is based on NFPA requirements; however, during accelerator operations, many areas are inaccessible, and maintenance scheduling is predicated on access times. All contractually required inspections and tests are accomplished during available maintenance periods.
· NFPA 10 Standard for Portable Fire Extinguishers, 2013 Edition
· NFPA 12 Standard on Carbon Dioxide Extinguishing Systems, 2011 Edition
· NFPA 17A Standard for Wet Chemical Extinguishing Systems, 2013 Edition
· NFPA 25 Standard for the Inspection Testing, and Maintenance of Water-Based Fire Protection Systems, 2014 Edition
· NFPA 72 National Fire Alarm and Signaling Code, 2013 Edition
· NFPA 80 Standard for Fire Doors and other Opening Protectives, 2013 Edition
· NFPA 105 Standard for the Installation of Smoke Door Assemblies and Other Opening Protectives, 2013 Edition
· NFPA 291 Recommended Practice for Fire Flow Testing and Marking of Hydrants, 2013 Edition
· Fire Protection Handbook 20th Edition, ©2008 National Fire Protection Association
7.0 Revision Summary
Revision 0.1 - 09/17/13 - Periodic Review – Clarified Responsibilities and Expectations; updated links.
REVIEW REQUIRED DATE
Fire Protection Dept